Trussville’s Choice for HVAC
for Trussville, AL
Performed (1) system maintenance. Checked chambers, all electrical components, flushed drains, and checked duct system. Found run capacitor outside of range and blower wheel very dirty.
Fan motor with blade
Standard tune Up
NEEDED A TUNE UP ON SYSTEM.
Went to do a diagnostic because of a no cooling problem.
Came out to do estimate on system and replaced it.
2 system Change out pulled out the old systems and replaced them with 2 Amana systems.
20 point inspection of cooling and heating system
no cooling repairing of compressor
no cooling on ac system
repairing pvc line for AC unit